Panic at Three Mile Island
Panic at Three Mile Island
- Page created by EMW, 5 September 2008
- Contributors: EMW x3, Nbrewer x5, Administrator1 x4
- Last modified by Administrator1, 22 July 2014
The accident was caused by a combination of factors such as equipment malfunctions, design problems, and operator mistakes. It led to significant damage to the reactor core but only very small off-site releases of radioactivity. The accident began about 4:00 a.m, when the plant experienced a failure in the secondary, non-nuclear section of the plant. The main feedwater pumps stopped running, caused by either a mechanical or electrical failure, which prevented the steam generators from removing heat. First the turbine, then the reactor automatically shut down. Immediately, the pressure in the primary system (the nuclear portion of the plant) began to increase. In order to prevent that pressure from getting too high, a relief valve opened. The valve should have closed when the pressure decreased by a certain amount, but it did not. Signals available to the operator failed to show that the valve was still open. As a result, the stuck-open valve caused the pressure to continue to decrease in the system.
Because adequate cooling was not available, the nuclear fuel overheated to the point where some of the zirconium cladding (the long metal tubes or jackets that hold the nuclear fuel pellets) reacted with the water and generated hydrogen. This hydrogen was released into the reactor containment building. By 30 March, two days after the start of the chain of events, some hydrogen remained within the primary coolant system in the vessel surrounding the reactor, forming a “hydrogen bubble” above the reactor core. The concern was that if reactor pressure decreased, the hydrogen bubble would expand and interfere with the flow of cooling water through the core.
Response to the accident was swift. By 8:00 a.m., the NRC headquarters in Washington, DC, was alerted. At 9:15 a.m., the White House was notified and at 11:00 a.m., all non-essential personnel were ordered off the plant’s premises. Friday, 30 March, Governor Thornburgh of Pennsylvania ordered a precautionary evacuation of preschool children and pregnant women from within the 5-mile zone nearest the plant, and suggested that people living within 10 miles of the plant stay inside and keep their windows closed. Over 100,000 panic-stricken residents fled the area. Most evacuees were able to return to their homes by April 4. By that time, the situation at the reactor had been brought under control.
Comprehensive investigations have shown that in spite of serious damage to the reactor, most of the radiation was contained and that the actual release had negligible effects on the physical health of individuals or the environment.
By far, the greatest casualty of the accident at Three Mile Island was public confidence in nuclear power. The accident permanently changed both the nuclear industry and the NRC. Public fear and distrust increased, NRC’s regulations and oversight became broader and more robust, and management of the plants was scrutinized more carefully. Increased regulatory oversight has led to huge increases in the cost of operating nuclear plants and has led many utilities to cancel or abandon planned nuclear power stations.
<rating comment="false"> Well Written? 1 (No) 2 3 4 5 (Yes) </rating> <rating comment="false"> Informative? 1 (No) 2 3 4 5 (Yes) </rating> <rating comment="false"> Accurate? 1 (No) 2 3 4 5 (Yes) </rating>